7TACOM.DLL:



   - 2010-05-03:

     POLLED: Updated for Flygt AquaCom.



   - 2010-05-18:

     POLLED: Updated for Flygt AquaCom.



7TACOMC.DLL:



   - 2010-05-18:

     POLLED: Updated for Flygt AquaCom.



7TCMLTCP.DLL:



   - 2009-10-26:

     Driver is unable to start. Driver log shows either a crash (if IGSS
version 

     7 is installed on the PC) or an error message with error number 126
while starting.

      This has now been fixed.



   - 2011-10-10:

     TT2183 : Increased number of channels/nodes from 150 to 1024.
Request from Niels 

     Mshlgaard, MJK.



   - 2013-01-28:

     risk overrun buffer possible control flags lock



7TCMLTCPC.DLL:



   - 2011-09-30:

     7TCMLTCP: Increased number of channels/nodes from 150 to 1024.



7TDHFILE.DLL:



   - 2009-09-02:

     The 7TDHFILE driver now also supports STRINGS. The external type
must be enables 

     as a valid 8 bit type in system configuration - and you must use
external type 

     FP8 for all string objects mapped to sting values in the input
file. STRINGs 

     must be specified as type 3 in the input file.



   - 2010-05-11:

     Added support for "IGSSTAG" input tag format.



   - 2010-05-18:

     Added support for "IGSSTAG" input tag format.



   - 2010-06-14:

     Time stamp is updated when file is changed, not with the date /
time from file:

      (0, 0, 0, 21-april-2010, 14:47:00.00). If Dword value was lower
than 65536 

     the driver filed.



   - 2010-08-12:

     Minor changes to correct some formatting issues.



7TDHFILEC.DLL:



   - 2009-09-02:

     The 7TDHFILE driver now also supports STRINGS. The external type
must be enables 

     as a valid 8 bit type in system configuration - and you must use
external type 

     FP8 for all string objects mapped to sting values in the input
file. STRINGs 

     must be specified as type 3 in the input file.



   - 2010-05-11:

     Added support for "IGSSTAG" input tag format.



   - 2010-05-18:

     Added support for "IGSSTAG" input tag format.



   - 2010-06-14:

     Time stamp is updated when file is changed, not with the date /
time from file:

      (0, 0, 0, 21-april-2010, 14:47:00.00). If Dword value was lower
than 65536 

     the driver filed.



7TDRV.EXE:



   - 2010-08-12:

     Some drivers (7TDHFILE and 7TOPC) might throw exceptions during
shut down. This 

     has now been fixed.



   - 2011-01-25:

     TT2041 :Time services not working with DialUp and GPRS



7TFGW.DLL:



   - 2011-02-17:

     TT2386 : Increased number of independent channels to 128.



7TFT2000.DLL:



   - 2010-04-13:

     Driver crashing on machines with multiple cores. WriteFile and
ReadFile used 

     the same overlapped structure resulting in wrong number of
transfered bytes 

     and ultimately a crash



   - 2010-05-18:

     Driver crashing on machines with multiple cores. WriteFile and
ReadFile used 

     the same overlapped structure resulting in wrong number of
transfered bytes 

     and ultimately a crash



7TIZU.DLL:



   - 2009-09-16:

     Due to a memory overwrite the driver try to fetch data from random
datagroups 

     if the user requested data from data group 15.



7TMELSQ.DLL:



   - 2009-10-23:

     Major update of protocol stack.



7TMELSQC.DLL:



   - 2009-10-23:

     Major update of protocol stack.



7TMJKTCP.DLL:



   - 2011-02-10:

     The 7TMJKTCP driver might crash in rare situations. A relatively
high risk of 

     crash is seen if a specific node continue to be unreachable for
extensive amounts 

     of time (ie. several days/weeks).  This has now been fixed.



   - 2012-09-26:

     Pump stations that run driver 54 (MJK grps) will not link up with
the 10 min 

     interval as they are set up. 

     Now it will try multiple times to connect if 

     connection is bad  

     



7TMOD.DLL:



   - 2010-05-25:

     Support for Grundfos CU361 devices in 7Tmod and 7Tmodgprs



   - 2010-11-10:

     7TMOD using wrong Modbus ID for PLCs when connected directly



   - 2011-02-17:

     TT2256: Support for new CU25X Grundfos PLCs in 7TMOD and 7TMODGPRS



7TMODC.DLL:



   - 2010-05-25:

     Support for Grundfos CU361 devices in 7Tmod and 7Tmodgprs



   - 2010-11-10:

     7TMOD using wrong Modbus ID for PLCs when connected directly



   - 2011-02-17:

     TT2256: Support for new CU25X Grundfos PLCs in 7TMOD and 7TMODGPRS



7TMODEXT.DLL:



   - 2012-09-26:

     If PLC is longer than 6000 MS to answer IGSS driver will time out.

     IGSS will 

     now write in Driver76.log how long the answer time is the log will
look like 

     this:

     readComm chan:1 timeout:7094 nBytesRead:-1 errGrp:22 errRc:995

     

     The 

     Answer time is = 7094 MS you can extend the answer time in
registry. 

     

     Remember 

     to set it for ALL cannels and give it a bit extra, if time out is
7094 MS give 

     it 10000 MS.

     

     HKEY_CURRENT_USERSoftware7-TechnologiesIGSS32V8.00.007TMODEXT_

     HKLMChannel0

     Set RecvTimeout=10000

     

     HKEY_CURRENT_USERSoftware7-Technologies

     IGSS32V8.00.007TMODEXT_HKLMChannel1

     RecvTimeout=10000

     



7TMODGPRS.DLL:



   - 2010-06-08:

     Driver sometimes stops scanning the device requiring restart of
driver



   - 2010-07-07:

     Driver sometimes stops scanning the device requiring restart of
driver



   - 2010-08-04:

     7TMODGPRS driver stops polling if GPRS connection drops



   - 2010-08-12:

     Communications error when TCP Header is received without main
packet



   - 2011-02-17:

     TT2256: Support for new CU25X Grundfos PLCs in 7TMOD and 7TMODGPRS



   - 2011-09-26:

     7TMODGRPS : Keepalive gets sent as a MODBUS write instead of MODBUS
read, and 

     getting history sometimes fails



7TMODGPRSC.DLL:



   - 2011-02-17:

     TT2256: Support for new CU25X Grundfos PLCs in 7TMOD and 7TMODGPRS



7TOMRTCP.DLL:



   - 2010-03-10:

     New Driver 85 (7TOMRTCP)



   - 2010-04-12:

     Driver might crash if network interface is disabled while the
driver is running.

      This has now been fixed.



   - 2010-05-18:

     Driver might crash if network interface is disabled while the
driver is running.

      This has now been fixed.



   - 2010-10-27:

     Extended the field description to clear up why there is two
bitoffsets.



   - 2010-11-04:

     Added decription of Bit offset



   - 2011-05-09:

     -



7TOMRTCPC.DLL:



   - 2010-03-10:

     New driver 85 (7TOMRTCP)



   - 2010-04-12:

     The valid IGSS Node address is now limited to 1..127.



   - 2010-05-18:

     The valid IGSS Node address is now limited to 1..127.



   - 2010-11-04:

     Added decription of Bit offset



7TOPC.DLL:



   - 2009-10-05:

     7TOPC cannot connect to a SimaticNet OPC running in 2003 server in
a VMware 

     image

     Initial Security settings changed



   - 2009-10-14:

     OPC driver sometimes failed to reconnect to a server if the server
has been 

     restarted



   - 2009-10-16:

     OPC option "Allen Bradley no VT_ARRAY" option does not work when
updating tables 

     from Grid descriptor or VBA unless DC registry FullTable is set

     

     Grid descritor 

     and VBA sends table items one by one.All other places all table
items is send 

     together The driver has now been changed so that both scenarios are
handled 

     and the state of the FullTable registry setting can be ignore



   - 2009-12-02:

     Changes to tables are not always accepted by OPC server when using
OPC driver

     

     

     Length of safe array sent to OPC driver was too long. Some dirvers
(Merz for 

     SAIA) will the discard data without any notice

     



   - 2010-01-06:

     OPC tables are no longer indexed incorrectly from embedded
diagrams.



   - 2010-04-22:

     All or most OPC addressing in the configuration are at rare cases
deleted at 

     start up



   - 2010-04-22:

     Option to driver 42(OPC) so it can read CU401 CSV files backwards



   - 2010-05-18:

     All or most OPC addressing in the configuration are at rare cases
deleted at 

     start up

     New option to driver 42(OPC) so it can read CU401 CSV files
backwards

     

     

     



7TPS4.DLL:



   - 2009-12-15:

     Kr'ger has updated a configuration from V6 to V8 and Historic data
wouldnt work 

     thereafter  turns out that the Nodes registry was longer than the
buffer allocated 

     for it -  buffer size raised from 200 to 400

     



7TS7TCP.DLL:



   - 2009-11-16:

     Max number of nodes expanded to 256.

     When setting up these nodes, take into 

     consideration that all traffic pass thru only one ethernet card and
there is 

     a max limitation in windows on 10 connection requests at the same
time.

     



   - 2011-09-26:

     7TS7TCP: Driver alarm if CPU is in STOP.



   - 2012-02-06:

     The 7TS7TCP driver might fail on very slow networks. The problem
will normally 

     be reported as a temporary driver alarm - BUT communication might
stop permanently 

     in some cases.



7TS7TCPC.DLL:



   - 2009-11-16:

     Max number of nodes expanded to 256.

     When setting up these nodes, take into 

     consideration that all traffic pass thru only one ethernet card and
there is 

     a max limitation in windows on 10 connection requests at the same
time.

     



   - 2012-09-10:

     Fixes: edit mapping dialogue of S7TCP driver is too big so some of
the controls 

     are outside the dialogue



7TS7TSA.DLL:



   - 2009-10-22:

     MPI Network segment ID can now be set to 0



   - 2010-10-06:

     Driver could fail when receiving inbound connections (dialin)



7TS7TSAC.DLL:



   - 2009-10-22:

     MPI Network segment ID can now be set to 0



7TTCPMON.CHM:



   - 2009-11-02:

     The help file for the IGSS Soft PLC, 7TTCPMON, has been revised
with more setup 

     procedures. Also, a PDF output is now available.



7TTCPMON.EXE:



   - 2009-12-10:

     7TTCPMON now has a "Help" button and a help file for the user.



ACCCTRL8.DLL:



   - 2009-10-16:

     Audittrail SQL server settings was not replicated correctly from
server to OP/

     thin clients.



   - 2009-11-12:

     Definition: Missing OPC tags after copy and rename of an object. If
you copy 

     and rename (or just rename) an object with one or more atoms mapped
to OPC tags 

     then the OPC tags are lost. This has now been fixed.



   - 2009-11-13:

     Correct cheksum



   - 2010-03-12:

     AuditTrail DB handling might crash applications if Audit Trail DB
connection 

     fails. This has been fixed.



   - 2010-09-02:

     You could unintensionally change the number of an alarm in the edit
alarm dialogue.



   - 2011-02-16:

     Alarm: Posibility to add 100 conditions in the Alarm filter



   - 2011-04-08:

     Mnt: Crash when trying to create Filters. This is now fixed



   - 2011-09-16:

     -



ALARMMANAGEMENTSYSTEM.EXE:



   - 2009-11-04:

     AMS with 3 new features: Dutyplans across midnight, Calendar active
states from 

     IGSS object and GetValue by SMS from IGSS object. See AMS help for
further infomation.



   - 2009-11-27:

     Save of atom of set value corrected.



   - 2009-11-30:

     x



   - 2009-12-03:

     Change of existing atom for send commands is now saved.



   - 2010-03-22:

     Language update.



   - 2010-04-21:

     Update that fixes cycle in callback message rutine.



   - 2010-05-18:

     Update that fixes cycle in callback message rutine.



   - 2010-05-25:

     Improved stability on 64bit Windows.



   - 2010-08-18:

     Decreased delay until Alarm Ended SMS is sent.

     Better creation of similare 

     duties when exception day is set.

     Paste of 24 hour duties no longer cut to 

     fit current date.

     Possibility to specify reg password required to stop/exit 

     AMS.



   - 2010-11-16:

     You now have the possibility to change alarm priority in AMS when
server is 

     not accesible. 

     

     Set the following setting i registry (the "12" is the actual 

     priority)

     

     [HKEY_CURRENT_USERSoftware7-TechnologiesIGSS32v8.00.00AMS

     Settings]

     "ServerErrorPriority"="12"

     



   - 2010-12-10:

     AMS somtimes converts the type form a weekly based type to a Daily
type and 

     period to 8 days. This is now fixed



   - 2011-02-14:

     AMS does not always send message to operator, when his duty is on.
Eventhough 

     AMS is set to do so under settings, This has now been fixed

     



   - 2011-03-15:

     Calendar only mode by adding registry string
AMS/Settings/CalendarMode with 

     values 1 or 2. Save now works as Save, and not Save As... Special
Options added 

     to send daily status message to Supervisor or active primary
operators. Bugfix 

     for Operator on Duty SMS for duties passing midnight.



   - 2011-06-06:

     New AMS features. Dual Server support. Regsettings for AutoSave and
3 CalendarModes.



   - 2011-06-07:

     Re-upload of latest AMS.



   - 2011-12-12:

     -



   - 2012-01-10:

     AMS did not re-initialize Mmdem in case of modem being switched off
and on. 

     This update corrects this.



ALARMMANAGEMENTSYSTEM.RESOURCES.DLL:



   - 2009-09-24:

     Updates to Danish language version



   - 2009-09-24:

     Updates to German language version



   - 2009-09-24:

     Updates to Spanish language version



   - 2009-11-04:

     Czech version of AMS updated with new texts for new features.



   - 2009-11-04:

     Danish version of AMS updated with new texts for new features.



   - 2009-11-04:

     German version of AMS updated with new texts for new features.



   - 2009-11-04:

     Icelandic version of AMS updated with new texts for new features.



   - 2009-11-04:

     Norwegian version of AMS updated with new texts for new features.



   - 2009-11-04:

     Polish version of AMS updated with new texts for new features.



   - 2009-11-12:

     Updates to German language version



   - 2009-11-12:

     Updates to Czech language version



   - 2009-11-12:

     Updates to Norwegian language version



   - 2009-11-19:

     Language update for German version of AMS



   - 2010-02-15:

     Updates to Norwegian language version



   - 2010-03-19:

     Spanish language update for AMS module in IGSS



   - 2010-03-19:

     Polish language update for AMS module in IGSS



   - 2010-03-19:

     Swedish language update for AMS module in IGSS



   - 2010-03-19:

     Russian language update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-03-22:

     Language Update



   - 2010-04-23:

     Swedish AMS language update



   - 2010-05-18:

     Swedish AMS language update



   - 2010-08-18:

     AMS Danish Language file



   - 2011-03-15:

     AMS danish language update.



   - 2011-06-06:

     New AMS features. Dual Server support. Regsettings for AutoSave and
3 CalendarModes.



   - 2011-06-07:

     Re-upload of latest AMS.



   - 2012-01-10:

     AMS - Danish language for Defect 2977.



ALM.CHM:



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



ALM.EXE:



   - 2009-08-27:

     Event list formats are not correctly saved or loaded

     

     New registry setting 

     "Use Black for White" in Alarm32_HKLM.

     By default it is 0 an giving the original 

     funtionalite

     If it set to 1 acknowledged alarm defined with an acknowledge 

     colour of white will be shown in black

     

     It should optionally be possible to 

     acknowled online alarms appearing in the alarm history

     

     A new registry setting 

     "Ticks between hist updates" has been added to Alarm32_HKLM

     By default it is 

     0 and the original funtionality is assumed - that is no automatic
update of 

     history list

     If it is set >0 the list will automatically be updateafter the 

     number of timer ticks specified. A timer tisck is by default 450
msec and can 

     be read from the "TimerTick" registry setting

     

     If showEvent registry is set 

     to 0 the toolbars are not shown any more



   - 2009-09-16:

     Spelling errors in alarm acknowledgement audit trail when set to
English language 

     has been fixed



   - 2010-07-23:

     Horizontal scroll bar was missing in the alarm list when the event
list has 

     been disabled. This has now been fixed.



   - 2010-11-05:

     Alarm: Support for substituting the event list with an extra alarm
list.

     

     

     Support for substituting the event list with an extra alarm list
has been added.

       If the registry setting Alarm32_HKLMsubstEvtWithExtraAlmList
(default value 

     is 0 - disabled) is set to 1 (enabled) then the standard event list
is substituted 

     with an extra alarm list thus enabling the user to see two
identical alarmlists.

      The topmost alarm list shows all alarms with priority less than
200 and the 

     lower alarm list shows all alarms with priority higher than 200. 
The idea is 

     that you can use the lower alarm list to show eventlit like alarms
- i.e. normally 

     auto ack'ed alarms.



   - 2010-11-22:

     Support for substituting the event list with an extra alarm list
has been added.

       If the registry setting Alarm32_HKLMsubstEvtWithExtraAlmList
(default value 

     is 0 - disabled) is set to 1 (enabled) then the standard event list
is substituted 

     with an extra alarm list thus enabling the user to see two
identical alarmlists.

      The topmost alarm list shows all alarms with priority less than
200 and the 

     lower alarm list shows all alarms with priority higher than 200. 
The idea is 

     that you can use the lower alarm list to show event-like alarms -
i.e. normally 

     auto ack'ed alarms.



   - 2011-02-16:

     Alarm: Posibility to add 100 conditions in the Alarm filter



ALMAPI8.DLL:



   - 2010-06-29:

     DEF Supervice sometimes crashes if Graph Axis Proberties (Period)
are changed 

     before graph appears



AMS.CHM:



   - 2009-08-10:

     There was a "Page not found" error on the startup page of the help
file. This 

     has been fixed.



AMS.CHM:



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



AMS.CHM:



   - 2009-11-04:

     The AMS help file has been revised as follows:  

     - The feature that allows 

     you to receive SMS alarms from 3rd party SCADA systems is now fully
documented

     

     

     - It is now possible to get values from IGSS objects via SMS

     - Duty periods 

     crossing midnight can be drawn directly in calendar view

     - You can now switch 

     calendars by SMS using the Calendar Object in IGSS

     - PDF output of the help 

     file now available  



AMS.CHM:



   - 2009-11-04:

     The AMS help file has been revised as follows:  

     - The feature that allows 

     you to receive SMS alarms from 3rd party SCADA systems is now fully
documented

     

     

     - It is now possible to get values from IGSS objects via SMS

     - Duty periods 

     crossing midnight can be drawn directly in calendar view

     - You can now switch 

     calendars by SMS using the Calendar Object in IGSS

     - PDF output of the help 

     file now available  



APMSGW8.DLL:



   - 2012-09-26:

     If PLC is longer than 6000 MS to answer IGSS driver will time out.

     IGSS will 

     now write in Driver76.log how long the answer time is the log will
look like 

     this:

     readComm chan:1 timeout:7094 nBytesRead:-1 errGrp:22 errRc:995

     

     The 

     Answer time is = 7094 MS you can extend the answer time in
registry. 

     

     Remember 

     to set it for ALL cannels and give it a bit extra, if time out is
7094 MS give 

     it 10000 MS.

     

     HKEY_CURRENT_USERSoftware7-TechnologiesIGSS32V8.00.007TMODEXT_

     HKLMChannel0

     Set RecvTimeout=10000

     

     HKEY_CURRENT_USERSoftware7-Technologies

     IGSS32V8.00.007TMODEXT_HKLMChannel1

     RecvTimeout=10000

     



AUDITTRAIL.CHM:



   - 2009-08-13:

     The Audit Trail help file, AuditTrail.chm, was mistakenly not part
of the release 

     installation program. 



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



   - 2010-02-09:

     When adding the Audit Trail database to the SQL Server, there are a
number of 

     decisions and considerations to be made. They have now been
integrated in the 

     user documentation.



AUDITTRAIL.EXE:



   - 2009-08-14:

     On some (typically faster) computers, the Audit Trail application
would lock 

     during start-up of the system.



   - 2009-08-17:

     When language is set to Polish in SysConfig the Dashboard and
Audittrail applications 

     crashes during start-up.



   - 2009-09-15:

     AuditTrail application now uses blue color theme as default



   - 2009-09-15:

     Audittrail object browser columns too narrow



   - 2010-03-05:

     Audit Trail app would not connect on operator station when sql
server authentification 

     was enabled - this has been fixed.



   - 2010-03-10:

     AuditTrail connection to SQL server using Windows Authentification
would not 

     work after fix from Monday - this has been corrected.



AUDITTRAIL.RESOURCES.DLL:



   - 2009-09-22:

     Updates to Polish language version.



   - 2009-09-22:

     Updates to Norwegian language version.



   - 2009-09-24:

     Updates to Czech language version



   - 2009-09-24:

     Updates to Danish language version



   - 2009-09-24:

     Updates to German language version



   - 2009-09-24:

     Updates to Spanish language version



   - 2009-10-20:

     Audit Trail and Dashboard now available in Swedish.



   - 2009-11-12:

     Updates to German language version



   - 2009-11-19:

     Language update for Polish version of AuditTrail



   - 2010-03-19:

     Updates for French language



   - 2010-03-19:

     Russian language update



   - 2010-03-19:

     French language updated



   - 2010-03-31:

     Fixed some russian UI problems in Audit Trail and Dashboard



AUDITTRAILLIB.DLL:



   - 2009-08-17:

     When language is set to Polish in SysConfig the Dashboard and
Audittrail applications 

     crashes during start-up.



   - 2009-09-15:

     When the report folder set in SysConfig was not valid, an exception
would be 

     displayed when launching the AuditTrail application.



   - 2009-09-15:

     AuditTrail should use English help file if local language help file
is not avail

     able



   - 2009-09-16:

     The character used to separate different periods in the Audittrail
period combobox 

     looked strange on some computers. The character has been changed to
a small 

     dot which looks more consistent.



   - 2010-03-05:

     Audit Trail app would not connect on operator station when sql
server authentification 

     was enabled - this has been fixed.



   - 2010-03-10:

     AuditTrail connection to SQL server using Windows Authentification
would not 

     work after fix from Monday - this has been corrected.



AUDITTRAILLIB.RESOURCES.DLL:



   - 2009-09-22:

     Updates to Polish language version.



   - 2009-09-22:

     Updates to Norwegian language version.



   - 2009-09-24:

     Updates to Czech language version



   - 2009-09-24:

     Updates to Danish language version



   - 2009-09-24:

     Updates to German language version



   - 2009-09-24:

     Updates to Spanish language version



   - 2009-10-20:

     Audit Trail and Dashboard now available in Swedish.



   - 2009-11-26:

     Updates to Norwegian language version



   - 2010-03-19:

     Updates for French language



   - 2010-03-19:

     Russian language update



   - 2010-03-19:

     French language updated



   - 2010-03-31:

     Fixed some russian UI problems in Audit Trail and Dashboard



BCLMERGE.EXE:



   - 2010-01-11:

     New Command line utility that can merge BCL files from two
configurations that 

     have benn merged into one



CALENDAR.DAYVIEW.DLL:



   - 2009-11-04:

     AMS with 3 new features: Dutyplans across midnight, Calendar active
states from 

     IGSS object and GetValue by SMS from IGSS object. See AMS help for
further infomation.



   - 2009-11-27:

     Save of atom of set value corrected.



   - 2009-11-30:

     x



   - 2010-03-22:

     Language update for AMS.



   - 2010-04-21:

     Update that fixes cycle in callback message rutine.



   - 2010-05-18:

     Update that fixes cycle in callback message rutine.



   - 2010-05-25:

     Improved stability on 64bit Windows.



   - 2010-08-18:

     AMS Calendar file



   - 2011-03-15:

     Calendar only mode by adding registry string
AMS/Settings/CalendarMode with 

     values 1 or 2. Save now works as Save, and not Save As... Special
Options added 

     to send daily status message to Supervisor or active primary
operators. Bugfix 

     for Operator on Duty SMS for duties passing midnight.



   - 2011-06-06:

     New AMS features. Dual Server support. Regsettings for AutoSave and
3 CalendarModes.



   - 2011-06-07:

     Re-upload of latest AMS.



   - 2012-01-10:

     AMS did not re-initialize Mmdem in case of modem being switched off
and on. 

     This update corrects this.



CHELM.CHM:



   - 2009-11-23:

     The help file about the Chelm module (Install Configuration) has
been updated 

     and a PDF Output is now also available.



CHELM.EXE:



   - 2011-02-15:

     You can now specify alarm number in both input and local mode

     However for backward 

     compatibility with configurations having specified these atoms as
local but 

     specified no alarm number there can be no validation of this.

     Only if you specify 

     an alarm number it is validated.



   - 2011-11-17:

     New function added for calculations:

     

     STRING MyName()

     

     Returns the name 

     of the object that executes the calculation as a STRING.

     

     The purpose of this 

     function is to allow syntax like this:

     

     AnaValue(MyName())

     

     this composit 

     expression should return the (double) value of the "Free Value"
atom if executed 

     on ANY atom on a digital obejct.



   - 2012-11-05:

     Alarm delay on driver object fixed. 



CNVTO8.EXE:



   - 2009-11-06:

     When converting configurations from version 6/7 to version 8,
buttons that had 

     external commands configured were not converted correctly causing
the external 

     command to be missing in version 8. This has been fixed.



COMMDRV84-85.REG:



   - 2010-03-10:

     Support for new driver 85 (7TOMRTCP)



CSYACTRL.DLL:



   - 2009-09-02:

     Some translations were missing in the Czech language version.



   - 2009-09-24:

     Updates to Czech language version



CSYCHLM.DLL:



   - 2009-09-24:

     Updates to Czech language version



CSYDC.DLL:



   - 2009-11-12:

     Updates to Czech language version



CSYDEF.DLL:



   - 2009-08-17:

     Fixes an isssue with a CSY translation og a dialog in IGSS.



   - 2009-09-03:

     The Edit Event dialog box had layout problems in the Czech version.



   - 2009-09-24:

     Updates to Czech language version



   - 2009-11-12:

     Updates to Czech language version



   - 2011-02-04:

     Object Historian resize form - language verified



CSYIGSS.DLL:



   - 2009-09-24:

     Updates to Czech language version



   - 2009-11-12:

     Updates to Czech language version



CSYWINPG.DLL:



   - 2009-09-24:

     Updates to Czech language version



DANACTRL.DLL:



   - 2009-09-02:

     Some translations were missing in the Danish language version.



   - 2009-09-24:

     Updates to Danish language version



DANALARM.DLL:



   - 2009-09-24:

     Updates to Danish language version



DANCHLM.DLL:



   - 2009-09-24:

     Updates to Danish language version



DANDC.DLL:



   - 2009-09-24:

     Updates to Danish language version



DANDEF.DLL:



   - 2009-08-14:

     There was a layout problem in the Multi-Screen Setup
(Flerskzhrmsopszhtning) dialog 

     box in the Danish version.



   - 2009-08-17:

     Fixes a missing Danish translation where a dialog would force IGSS
to close.



   - 2009-08-21:

     Layout problems have been fixed in the Danish version.



   - 2009-09-03:

     The Edit Event dialog box had layout problems in the Danish
version.



   - 2009-09-24:

     Updates to Danish language version



   - 2009-09-29:

     The text "Tillad ikke-proportionalt strzhk" must be changed to
"Tillad strzhk"

      on the Animated Symbol tab (Danish version).



   - 2010-03-19:

     Language update for Danish language version of IGSS module
Definition



   - 2011-02-23:

     The user can now be prompted to save the graph when he closes the
Dynamic Graph 

     window. A new Registry setting has been defined under
HKCU..DefRun32_HKLM

     PromptSaveDynGraphClose.

     

     It defaults to 0 which means no prompt to the user.

      If set to 1, the user will be prompted everytime he closes a
dynamic graph 

     with unsaved changes. He can then save the changes in a USR file.
If the dynamic 

     graph is opened from a USR file, the user will only be prompted if
any changes 

     have been made to the graph.



DANIGSS.DLL:



   - 2009-09-24:

     Updates to Danish language version



DANJOB.DLL:



   - 2009-09-24:

     Updates to Danish language version



DANWINPG.DLL:



   - 2009-09-24:

     Updates to Danish language version



DASHBOARD.CHM:



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



DASHBOARD.EXE:



   - 2009-08-17:

     When language is set to Polish in SysConfig the Dashboard and
Audittrail applications 

     crashes during start-up.



   - 2009-09-15:

     The Dashboard application could be launched multiple times which
would interfere 

     with the IGSS Starter logic



   - 2009-09-15:

     Dashboard should use English help file if local language help file
is not availa

     ble



   - 2009-09-15:

     The Dashboard will now show an error message when trying to create
a dashboard 

     with no name



   - 2009-09-15:

     Dashboard object browser columns too narrow



   - 2009-09-15:

     Dashboard snapshot widget showing too many atoms for string type
object in widget 

     setup ribbon



   - 2009-09-15:

     When creating a memo widget the text file is not created until you
edit the 

     memo text



   - 2009-09-15:

     Dashboard log and reduced widget columns are too narrow



   - 2009-09-16:

     The character used to separate different periods in the Dashboardl
period combobox 

     looked strange on some computers. The character has been changed to
a small 

     dot which looks more consistent.

     



   - 2009-11-29:

     Log widget does not show command and state names in text. This has
now been 

     fixed.



   - 2010-01-07:

     Disables unreleased trend widget...



   - 2010-02-09:

     Release of new Alarm Trend Widget and multi y-axis for graph widget
for the 

     Dashboard.



   - 2010-11-09:

     Dashboard froze sometimes when retrieving log-data



   - 2011-01-12:

     Autoscale on dashboard graphs was not working correctly on negative
numbers.



DASHBOARD.RESOURCES.DLL:



   - 2009-09-22:

     Updates to Norwegian language version.



   - 2009-09-24:

     Updates to Danish language version



   - 2009-09-24:

     Updates to German language version



   - 2009-09-24:

     Updates to Spanish language version



   - 2009-10-20:

     Audit Trail and Dashboard now available in Swedish.



   - 2009-11-12:

     Updates to Polish language version



   - 2009-11-12:

     Updates to Spanish language version



   - 2009-11-12:

     Updates to Norwegian language version



   - 2010-03-01:

     The Chelm (Install Configuration) module has now been translated
into French.



   - 2010-03-19:

     Russian language update



   - 2010-03-22:

     Czech language update for Dashboard module in IGSS



   - 2010-03-22:

     Danish language update for Dashboard module in IGSS



   - 2010-03-22:

     German language update for Dashboard module in IGSS



   - 2010-03-22:

     Spanish language update for Dashboard module in IGSS



   - 2010-03-22:

     French language update for Dashboard module in IGSS



   - 2010-03-22:

     Norwegian language update for Dashboard module in IGSS



   - 2010-03-22:

     Polish language update for Dashboard module in IGSS



   - 2010-03-22:

     Russian language update for Dashboard module in IGSS



   - 2010-03-22:

     Swedish language update for Dashboard module in IGSS



   - 2010-03-31:

     Fixed some russian UI problems in Audit Trail and Dashboard



   - 2010-05-07:

     Czech Dashboard language update



   - 2010-05-18:

     Czech Dashboard language update



DC.EXE:



   - 2009-09-17:

     To improve perfomance of reciving spooled data from distributed
drivers and 

     historical data from PLC's

     

     After this change it is not possible to combine 

     BCLdirect and BCLdelta.

     If you have specified BCLdirect, BCLdelta will be ignor

     ed



   - 2009-09-23:

     OPC tags are marked as "spooled" even if they are not.

     

     Some OPC servers send 

     zero values when the quality is bad.

     If you have a counter udes for reporting.

      The reports will be bad if such a zero is accepted

     Now the old value will 

     be kept but with the new quality stamp BAD



   - 2009-10-01:

     DC: Calculations might be triggered more than once on one the same
event.

     

     

     

     If you e.g. have a calculation expression on an object like this:
IIF(Value(

     'A1') > 200; 200; Value('A1')) then the calculation will be
triggered twice 

     if the actual value of A1 changes. This has now been fixed so the
execution 

     of the expression will only be triggered once.



   - 2009-10-14:

     Scan property on COM interface IGSSOBJECT was inverted when set



   - 2009-11-04:

     dc updated with new getvalue functionality for
AlarmManagementSystem



   - 2009-11-24:

     If you selected an alarmprinter in System Configuration you would
crash DC when 

     starting the system.



   - 2009-12-02:

     Tables with one entry does work with all OPC servers



   - 2009-12-08:

     The option "Mark objects with System Reset on Driver errors" might
cause the 

     system to log huge amounts of data if one or more PLC nodes were
disconnected 

     for longer periods of time. DC.EXE has now been changed in order to
ensure that 

     the SYSTEM RESET value is only written once to objects encountering
driver errors 

     (communication errors).



   - 2009-12-14:

     VBA atoms collection now includes high/low scale atoms



   - 2010-02-15:

     For tables the latest outgoing command was not logged.



   - 2010-02-18:

     Tables with alarm delay would never get into alarm



   - 2010-03-24:

     DC might fail in multiuser systems on Multi-CPU platforms in rare
occations.

      DC. The Application DC.EXE will crash, and sometimes you will get
an error 

     message from the Runtime Environment - sometimes no error message
will be given.

      Normally DC.EXE will be automatically restarted by the IGSS
starter, but OP 

     stations will temporarily loose connection to the server while
DC.EXE is being 

     restarted.



   - 2010-04-12:

     Analog node status objects with alarm delay might not work
correctly. This has 

     now been fixed.



   - 2010-04-16:

     DC might crash during system stop if AuditTrail is enabled. The
crash might 

     happen if the configuration was never loaded succesfully; e.g. if
the configuration 

     was not installed prior to deployment.



   - 2010-05-18:

     Analog node status objects with alarm delay might not work
correctly. This has 

     now been fixed.

     DC might crash during system stop if AuditTrail is enabled.

      The crash might happen if the configuration was never loaded
succesfully; e.

     g. if the configuration was not installed prior to deployment.

     



   - 2010-07-05:

     When an analog object get a bad quality vaue it will reuse the
existing value.

      This value will however get scaled once more if the is a scaling
object connected 

     t the analogue object



   - 2010-08-06:

     Spool progress indicator objects only worked when stationnames and
indicator 

     objects were in uppercase.



   - 2010-09-06:

     Graphs normaly based on BCL sometimes shows invalid data when based
on log (

     only on OP and with dataserver running)



   - 2010-09-30:

     Logfiles was defect after online configuration update



   - 2010-10-04:

     When an online configuration update was made, not all internal
structures (headerHash)

      was updated within the logfile machinery. The resulting defect
logfiles could 

     crash various programs reading them.



   - 2010-11-23:

     Ack of alarms which are inhibited behaves different depending on
whether the 

     alarm is acknowledged internally/locally from the alarm list or
externally from 

     the PLC.

     

     If the inhibited alarm is ack'ed using the alarm list (internal 

     ack) then the alarm get's ack'ed in the alarm list, but is stayes
in the alarm 

     list since the alarm has not been ended. If the inhibited alarm was
ack'ed externally 

     by the PLC by raising an alarm ack bit then the inhibited alarm
would be ack'

     ed and removed from the alarm list. The behaviour when ack'ing
inhibited alarms 

     externally has now been changed so that the alarm remains in the
alarm list 

     until ended regardsless if it is ack'ed internally or externally.



   - 2010-11-26:

     Logging didn't occur, in some scenarios, on new objects after an
update of the 

     configuration from an operator station to the server.



   - 2011-01-13:

     Baseclass reduction DIFFERENCE might be incorrect after server
restart. The 

     result of this problem is seen in both BCL files and in reports
containing report 

     objects based on DIFFERENCE reduction.  The problem is seen if the
server has 

     been stopped for more than one base class period and then restartet
again and:

       1) An object with data reduction DIFF has changed exactly one
time during 

     the server-down period and 2) The change is sent to IGSS with a
time stamp which 

     lies within the server-down period  A typical scenario for this is
if a new 

     project is deployed on the server and data is collected on a
distributed driver 

     station which uses the "spool data" function. Another typical
scenario is if 

     the data arrives as timestamped data from a logger device.  This
problem has 

     now been fixed.



   - 2011-01-24:

     After having uploaded a new configuration to the server a few
times, log files 

     are no longer added to. This has now been fixed.



   - 2011-02-11:

     Two scenarios are found an corrected.

     

     1.

        Seen when system is started 

     and shortly after (in the same BCL period) started again

        This is typically 

     seen in "online update"

        The data collected between the start of the BCL 

     reduction period and the stop time is not stored in BCL

     

     2.

       When DC enters 

     a cycle where it is supposed to finalize a BCL periode and a value
timestamped 

     in the

       few milliseconds between the start of the cycle and the actual
calculation.

      The value is not stored in BCL

     

     Both will give wrong calculation of differences 

     in reports.



   - 2011-02-16:

     When connecting as thin client with administrator priveledges on a
terminal 

     server, you can loose time. This has now been fixed with the
posibility to change 

     the registry setting: 

     HKEY_CURRENT_USERSoftware7-TechnologiesIGSS32V9.

     00.00DC_HKLM -> EnableIGSSTimeSynch = 0 on the station where you
don't want 

     to syncronice



   - 2011-02-18:

     When change of servers in a dualized system are needed the dialogue
will ask 

     for preferences It asks "primary server ... now available ..." It
should have 

     asked "connection to server .... lost ..."



   - 2011-02-18:

     DC can create a stack overflow on rare occations, if writing the
report directory 

     fails. This has now been fixed.



   - 2011-05-26:

     Department of Homeland Security's Industrial Control System Cyber
Emergency 

     Response Team has provided a pattern that when send to DC on TCP
port 12397 

     will popup a chelm.exe dialogue each time it is sent

     This dialogue require 

     user intervention to remove.



   - 2011-05-30:

     DC: StationObject can show wrong state, this is now fixed



   - 2011-06-06:

     Update on Operator Station failed, this is now fixed 



   - 2011-09-19:

     Some OPC needed restart before it collected data after online
update this is 

     now fixed

     Online Update to OP is tuned op.

     



   - 2012-06-20:

     Sometimes after changing configuration some of the objects don't
have report 

     data from midnigt and until the time of the change



   - 2013-01-11:

     DC security vulnerability on port 12397 reported by Aaron Portnoy,
Exodus Intelligence

     

     

     This is now fixed



DCM8.DLL:



   - 2009-10-09:

     Added support for EXTENDED Datapacket with OPC data quality



   - 2009-10-16:

     Sporadic missing log data leading to flat graphs



   - 2011-01-25:

     TT2041 :Time services not working with DialUp and GPRS



   - 2012-03-29:

     Driver logging leaking handles when stressed.

     This is now fixed.



DE.EXE:



   - 2009-07-28:

     Test V8 updater



   - 2010-02-08:

     DE: The de.exe application might fail if you have more than 32000
objects and 

     you are using Function Key Definitions.



   - 2010-04-19:

     DE removed two bound backgroundcolors of a textbox, this has been
fixed



   - 2010-05-18:

     DE removed two bound backgroundcolors of a textbox, this has been
fixed



   - 2011-06-09:

     DE has been extended to find and correct illegal fonts on
references to digital 

     states.



DEF.CHM:



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



   - 2009-10-14:

     The links to further information about VBA and Automation in the
"View VBA code"

      topic were broken. This has been fixed.



   - 2009-10-23:

     Fixed title of Safe Commands dialog option in Windows Registry
documented. "

     Change layout of periodical reports" topic finalized.



   - 2009-11-25:

     Viewing the spooling status and remaining spool time is a new
feature in IGSS 

     V8. The feature is now documented in the topic "The distributed
driver status 

     object (spooling status)" in the Definition Help file. The topic is
found in 

     the new book called "Objects with Special Functions".

     



DEF.CHM:



   - 2010-01-04:

     Before you start a new IGSS project, you should always go through
the "Checklist 

     for Planning a New IGSS Project". The checklist ensures that you
make the necessary 

     planning considerations and decisions. Experience has shown that if
you start 

     up the wrong way in IGSS, you end up using a lot of time correcting
your initial 

     mistakes. The motto is - do it right the first time. We know you
want to get 

     hands-on with the software, but the initial planning will save you
many hours 

     as the project proceeds.  The checklist is now included in the
Definition Help 

     file. The book is named "Checklist for Planning a New IGSS
Project". 



DEF.CHM:



   - 2010-02-01:

     Broken links in Valid Commands topics in the Definition help file.



DEF.CHM:



   - 2010-05-28:

     Fixed errors with table display of standard descriptor properties.



   - 2010-08-05:

     The Help text for the Online Suspend Node object now clearly
indicates that 

     the feature is not supported by event-based drivers.



   - 2010-09-07:

     More syntaxes to calculation feature are described in def.chm



   - 2010-09-08:

     Added description on calculation feature for counter objects and
how export/

     import of areas with CGF works.



DEF.EXE:



   - 2009-08-13:

     Two improvements have been added to the IGSS Data Server interface
(used for 

     standard graphs)

     

     1) Supervise now accepts that the IGSS Server address is 

     specified using the NETBIOS name of the IGSS Server instead of the
IP Address.

     

     

     2) If Supervise can't establish connection to IGSS Data Server then
diagnostic 

     information can be shown in a messagebox during startup of
Supervise. The message 

     box will ONLY be shown if the Ctrl key is down during the first few
seconds 

     activation of the Supervise application.



   - 2009-08-13:

     Two improvements have been added to the IGSS Data Server interface
(used for 

     standard graphs)

     

     1) Supervise now accepts that the IGSS Server address is 

     specified using the NETBIOS name of the IGSS Server instead of the
IP Address.

     

     

     2) If Supervise can't establish connection to IGSS Data Server then
diagnostic 

     information can be shown in a messagebox during startup of
Supervise. The message 

     box will ONLY be shown if the Ctrl key is down during the first few
seconds 

     activation of the Supervise application.



   - 2009-08-24:

     The table texts dosnt show when creating a table object and
selecting show table 

     tests.



   - 2009-09-07:

     Supervise might crash when user is shutting down the application
using close 

     icon in the upper right corner. This has now been fixed.



   - 2009-09-15:

     When a digital object was added to a grid with the 'unit with
value' option,

      a (null) would be displayed after the digital state.



   - 2009-09-15:

     When audit trail is enabled Supervise should not ask for
confirmation when local 

     command or set-point is changed.



   - 2009-09-15:

     Some texts were not localizable



   - 2009-09-21:

     When adding a group containing a group, to an third group, a crash
occurs.



   - 2009-09-23:

     Commands are missing in popup menu if object is in state numbers
above 32 if 

     valid commands have not been modified since the convertion from V7

     

     String 

     object values are not shown



   - 2009-09-30:

     Cursor no longer dissapears under the embedded alarm list



   - 2009-09-30:

     No you can have a fixed caption on the safe commands dialog.

     If you set HKEY_

    
CURRENT_USERSoftware7-TechnologiesIGSS32V8.00.00DefRun32_HKLMSafeCommand
Caption 

     to a string this will be shown instead of the object name.



   - 2009-10-02:

     Def might possibly crash if you have set the option
"ChgAreaAtDiaOpen" to 0 

     and you are copying an object from one area to another. This has
now been fixed.



   - 2009-10-13:

     When importing a group containing a polyline from one configuration
to another 

     Definition no longer crashes.



   - 2009-10-15:

     If all graphs are visible it just takes time to update them all
dymically

     If 

     the are distrubuted on many panes in an embedded diagram it has now
been optimized 

     so only graphs on the visible part of the pane will have their
graphics updated.

      



   - 2009-10-15:

     Graph data might be missing if IGSSDataServer is used and LOG file
size is very 

     big (10 Mb+). The problem is seen if it takes more than 1 second to
read a LOG 

     file from the report directory. The timeout has now been increased
to 10 secs.



   - 2009-10-16:

     A group box descriptor would have light gray background when set to
transparent.



   - 2009-10-19:

     When copying a text descriptor from a diagram of one size to a
diagram of a 

     different size the font size was not preserved even if you select
"Paste special"

      and check off "Preserve Proportions".  Same for all descriptors
having fonts.



   - 2009-10-19:

     Making new groupbox descriptors based on descriptor template made
inconsistensies 

     in the configuration - duble references in texts and fonts



   - 2009-10-27:

     Changing a setpoint using the keyboard up/down arrows would always
change in 

     steps of +/-1 whereas version 7 would change according to the
cursor position.

      This has been changed to be compatible with the version 7
behaviour.



   - 2009-10-27:

     Alarms on text objects with a set background color would blink to
transparent 

     instead of the alarm color. This has been fixed.

     



   - 2009-10-27:

     If you try to install a configuration in version 7 after installing
version 

     8 on that same pc you will get an version mismatch error as Def is
launching 

     chelm from the V8 folder. This has been fixed so that Def is using
the GSSWORK 

     folder setting in the registry.

     



   - 2009-11-02:

     The scroll bars on dynamic graphs does not act like you would
expect from scrollbars.

      This has now been fixed.



   - 2009-11-02:

     Supervise: Standard graphs: Setting graph end time to '00:00:00'
would add 24 

     hour to the graph data period.



   - 2009-11-10:

     Border on bargraph cannot be set transparent



   - 2009-11-10:

     Bargraphs: Border Properties set to transparent dosn't work.
Instead of transparent 

     the border was drawn with white color. This has now been fixed.



   - 2009-11-12:

     A new function has been added to the "Configuration" object

     

     Function SetAtomWithAudit(

     objName As String, AtomID, value) As Long

     

     ObjName: Name of the object to 

     change. Syntax is like when otherwise specifying objects in VBA

     AtomID:  atom 

     or table index to be changed. Either by number or name. Syntax is
like when 

     otherwise specifying atoms in VBA

     value:   new value of the atom. Any type 

     that can be converted to the relevant type can be used

     

     If AuditTrail or safe 

     command has been defined user will be promted and action will be
logged according 

     to settings.

     If the change is rejected  the function will return zero otherwise 

     different from zero

     



   - 2009-11-13:

     The first value on a standard graph might be missing if
IGSSDataServer is used 

     for fetching LOG values. This results in inaccurate trend graphs -
especially 

     if the object(s) graphed rarely changes (e.g. a digital state).
This has now 

     been fixed.



   - 2009-11-13:

     Correct cheksum



   - 2009-11-13:

     Correct cheksum



   - 2009-12-01:

     Def crashed if you tried to create a new graph but didn't have the
object "Graph"

      in your configuration.



   - 2009-12-08:

     VBA in configurations converted from v6 and earlier is opened in
VBA editor 

     each time defintion is started



   - 2009-12-11:

     Edit box descriptor was uneditable



   - 2009-12-15:

     Binding images to states pe buttons would ruin the name of the
global area



   - 2010-02-05:

     Embedded diagrams / sub diagrams were not updated when object found
via alarm

     

     

     Problem Solved



   - 2010-02-15:

     Alarm delay was working improperly for analog objects.



   - 2010-03-11:

     Adding item in graph, caused def to crash, this is now fixed



   - 2010-03-11:

     Import of groups containing graphs with certain properties may
crash



   - 2010-03-23:

     Command no. 31 not present when right click in supervise



   - 2010-03-25:

     When an OP has a certain set of diagrams open and the server is
disconnected 

     and reconnected the diagrams that are reopened are not shown
correctly.



   - 2010-03-26:

     DEF: Copy/Paste of descriptors referencing graph objects might
fail.



   - 2010-03-30:

     Can't add objects to USR graphs



   - 2010-04-16:

     DEF: Definition might crash if toolbar parameter database is
inconsistent or 

     corrputed.



   - 2010-04-22:

     DEF: Copy/Paste of descriptors referencing graph objects might
fail.



   - 2010-04-22:

     When selecting "Inspect" or "Export" from the right click menu of
an embedded 

     graph you get the popup message "Not implemented Yet!". Fixed.



   - 2010-05-18:

     DEF: Definition might crash if toolbar parameter database is
inconsistent or 

     corrputed.



   - 2010-06-02:

     Definition crashed if you imported a group exported by an early V7
into V8



   - 2010-06-24:

     Controling object for layers on reuseable diagram is not
replicated, but referensed.

      When changed it also changes the mother object, this has now been
fixed



   - 2010-06-29:

     DEF Supervice sometimes crashes if Graph Axis Proberties (Period)
are changed 

     before graph appears



   - 2010-07-30:

     When, bulk, changing the font size on descriptors in property table
view it 

     was a bit random what font size you actually ended up with on the
objects you 

     chose.

     

     - Some fonts was not scaled correctly

     - Some cells referenced fonts 

     that was not used. These can not be scaled correctly so now the are
marked with 

     "-" and cannot be edited

     

     Spool progress indicator objects only worked when 

     stationnames and indicator objects were in uppercase.



   - 2010-09-27:

     Views in reusable diagrams controlled by and object will initially
be controlled 

     by the view control object of the base group of the reusable
diagram instead 

     of the control object of the current instance, this has now been
fixed.



   - 2010-09-28:

     Corrupt LOG file made supervise crash



   - 2010-10-27:

     Def.exe crashed when using Ctrl-Z on embedded graphs repeatedly.



   - 2010-10-27:

     Supervise: Layers page should not be show in object properties
dialog if "ShowOnlyTypeSpecPages"

      is enabled. Note pages shall be shown.



   - 2010-11-09:

     Object value is not updated if a Graph window is moused over.



   - 2010-11-11:

     Def Crashed with MS webbrowser ActiveX both Ver 7 & 8



   - 2010-11-11:

     Definition crashed when copying a reusable diagram.

     

     Now the copy diagram 

     will be a standard diagram.



   - 2010-11-12:

     Def crashes when choosing viev VBA code from a button dsc. Win 7
x64 problem 



   - 2011-01-26:

     Supervise might crash in rare situations while adding or deleting
objects to 

     user defined graphs at runtime. This has now been fixed.



   - 2011-02-04:

     Sometimes the Online Update (several times) causes the definition
module to 

     crash. This has now been fixed



   - 2011-02-07:

     Sometimes there are a little latancy time from the configuration is
released 

     unitl the files are actually released on the disk.

     Definition will now retry 

     a few times before giving up.



   - 2011-02-07:

     -



   - 2011-02-09:

     Proberty Table view: When changing length and high on text
decriptors, it sometimes 

     results in change on other decriptors, this has now been fixed



   - 2011-02-16:

     Alarm: Posibility to add 100 conditions in the Alarm filter



   - 2011-02-18:

     -



   - 2011-02-18:

     A new regsetting has been defined
HKCU..DefRun32_HKLMPromptSaveDynGraphClose

     

     

     It default to 0 equal to the existing behaviour. i.e. no prompting
when closing 

     dynamic graphs.

     

     It it is set to 1 you will be prompted each time you close 

     a dynamic graph if he/she wants to save it as a USR file.

     If the dynamic graph 

     is opened from a USR file you will only be promted if you have made
any changes 

     to the graph after openening.



   - 2011-02-18:

     Option to open more than one user defined dynamic graph.

     

     By default all is 

     as before the change. You can have only one user defined dynamic
graph open 

     at a time  If you add extra graph objects in your "Global" area and
name them 

     with names prefixed by "Graph_" (eg. copy/paste default naming
Graph_1, Graph_

     2 etc.) you can have one extra user defined graph open for each of
the new objects.

      When you have used all of them and try to open one more the oldest
of the graphs 

     shown will be closed and the object reused. These graphs are also
included in 

     the total number of open windows. If you exeeds the maximum number
of open windows 

     graphs will also be closed. 



   - 2011-02-18:

     Setting of the the Keep Aspect proberty in Proberty Table View for
Area, could 

     cause the diagram to be resized, this has now been fixed.



   - 2011-02-21:

     To create diagrams wider than one screen you now have to enable the
multi monitor 

     mode.



   - 2011-03-07:

     Object historian continues to burn CPU after closing dialogue in
the middle 

     of a time consumning query. This has now been fixed



   - 2011-04-11:

     Def: Transparancy on Gif's is shown in def after IgssUpdate. This
is now fixed



   - 2011-05-03:

     Graphview: When opening a dynamic graph the proportions are not
keept the same 

     size when opening the second time, this is now fixed



   - 2011-05-03:

     -



   - 2011-06-09:

     Display Atom let you select Actule Value or set point



   - 2011-11-01:

     Def: V8 Not posible to make changes to default graph object (OK Btn
ignored)

     , This is now fixed



   - 2011-11-17:

     New function added for calculations:

     

     STRING MyName()

     

     Returns the name 

     of the object that executes the calculation as a STRING.

     

     The purpose of this 

     function is to allow syntax like this:

     

     AnaValue(MyName())

     

     this composit 

     expression should return the (double) value of the "Free Value"
atom if executed 

     on ANY atom on a digital obejct.



   - 2012-01-18:

     Paste/import object referenced by symbol descriptor some time show
a questionmark 

     instead of the symbol expected. 

     It happens paste tries to insert the pasted 

     symbol in a symbol tabel that is already full.

     The symbol will now be insterted 

     in another table

     If all existing tables are full you get a similar problem.

     

     Now new symbol tables are created on demand.



   - 2012-05-01:

     Previously, when setting a new set point for an analog object, the
digit to 

     the right of the cursor was changed when using the arrow-up and/or
arrow-down 

     keys. This could result in incorrect results when updating a
selection of digits 

     within the set point number.

     

     Now, the digit to the left of the cursor will 

     be updated when using the arrow-up and/or arrow-down key, allowing
you to select 

     a number of digits within the set point number and update the
selection incrementally 

     by u sing the arrow-up and/or arrow-down keys.

     



   - 2012-05-09:

     User defined Graph can save time change



   - 2012-09-18:

     If a object is member of more that 50 groups them member ships
require two or 

     more extension object.

     Only the first is included in the paste group



   - 2012-10-11:

     Changing object name adjustment in property table view does not
Work.

     Instead 

     the adjustment of the object value is changed



   - 2012-11-08:

     Bug Fix: Editbox descriptors does not work with string objects



DEF.TLB:



   - 2009-11-12:

     A new function has been added to the "Configuration" object

     

     Function SetAtomWithAudit(

     objName As String, AtomID, value) As Long

     

     ObjName: Name of the object to 

     change. Syntax is like when otherwise specifying objects in VBA

     AtomID:  atom 

     or table index to be changed. Either by number or name. Syntax is
like when 

     otherwise specifying atoms in VBA

     value:   new value of the atom. Any type 

     that can be converted to the relevant type can be used

     

     If AuditTrail or safe 

     command has been defined user will be promted and action will be
logged according 

     to settings.

     If the change is rejected  the function will return zero otherwise 

     different from zero

     



DEFINES.DLL:



   - 2012-01-10:

     AMS did not re-initialize Mmdem in case of modem being switched off
and on. 

     This update corrects this.



DEUACTRL.DLL:



   - 2009-09-02:

     Some translations were missing in the German language version.



   - 2009-09-24:

     Updates to German language version



DEUCHLM.DLL:



   - 2009-09-24:

     Updates to German language version



DEUDC.DLL:



   - 2009-11-12:

     Updates to German language version



DEUDEF.DLL:



   - 2009-08-17:

     Fixes an issue with the German translation of an IGSS dialog.



   - 2009-09-03:

     The Edit Event dialog box had layout problems in the German
version.



   - 2009-09-24:

     Updates to German language version



   - 2009-10-22:

     Layout corrected in German version (Diagram Properties and
Descriptor Properties)



   - 2009-11-03:

     German version: Definition crashed when trying to create a new
graph. Also there 

     was a layout problem in the Neue Kurveneigenschaften dialog box.



   - 2009-11-12:

     Updates to German language version



DEUIGSS.DLL:



   - 2009-09-24:

     Updates to German language version



   - 2009-11-12:

     Updates to German language version



DEUWINPG.DLL:



   - 2009-11-12:

     Updates to German language version



DMYREP.MDE:



   - 2010-10-06:

     V8 standard reports forced Duplex printing, even on printers with
no duplex 

     option.

     

     This have been reversed, if you want to print in duplex you have 

     to rename dmyrep_duplex.mde to dmyrem.mde.



DMYREP.MDE:



   - 2010-12-13:

     Printing Detailed yearly report, does not show data from 1. month.

     This issue 

     has now been fixed



DMYREP_DUPLEX.MDE:



   - 2010-10-06:

     V8 standard reports forced Duplex printing, even on printers with
no duplex 

     option.

     

     This have been reversed, if you want to print in duplex you have 

     to rename dmyrep_duplex.mde to dmyrep.mde.



DRAWG8.DLL:



   - 2010-04-29:

     Sometimes background drawings does not match the diagram size,
become semitransparent 

     or in other ways disturbed

     Use of BMP32 cashed images removed



   - 2010-05-18:

     Sometimes background drawings does not match the diagram size,
become semitransparent 

     or in other ways disturbed Use of BMP32 cashed images removed



   - 2011-02-16:

     DEF: If pictures contain text then the text are cut, this is now
fixed



   - 2011-04-11:

     Def: Transparancy on Gif's is shown in def after IgssUpdate. This
is now fixed



DRVEVENT.CHM:



   - 2009-11-13:

     The help file describing Event-Driven Communication with IGSS has
been revised.

      The help file is now available in PDF format. Simply click the
first item in 

     the Table of Contents, View as Printer-Friendly Version (PDF), to
view the file.

      The PDF file can be saved locally, if required.



ESPACTRL.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPALARM.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPCHLM.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPDC.DLL:



   - 2009-11-12:

     Updates to Spanish language version



ESPDEF.DLL:



   - 2009-08-17:

     Fixes a missing Spanish dialog translation that would cause IGSS to
close when 

     the dialog was opened.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Spanish language version.



   - 2009-09-24:

     Updates to Spanish language version



   - 2009-09-29:

     Layout problem in Diagram Properties (Spanish version).



ESPIGSS.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPJOB.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPMNT.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPMRE.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPQUICKSTART.PDF:



   - 2010-01-27:

     The Quick Start Guide has been revised. The vocabulary used in the
original 

     version did not match the existing IGSS terminology.



ESPUADM.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ESPWINPG.DLL:



   - 2009-09-24:

     Updates to Spanish language version



ETIDEF.DLL:



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Estonian language version.



FRAACTRL.DLL:



   - 2009-09-24:

     Updates to French language version



   - 2010-03-31:

     French is now completely translated in the modules: Alarm, Job
Scheduler, Maintenance 

     and User Administration. Some UI problems is also fixed in Access
Control



FRAALARM.DLL:



   - 2010-03-31:

     French is now completely translated in the modules: Alarm, Job
Scheduler, Maintenance 

     and User Administration. Some UI problems is also fixed in Access
Control



FRACHLM.DLL:



   - 2009-09-24:

     Updates to French language version



   - 2010-03-01:

     The Dashboard module has now been translated into French.



FRADC.DLL:



   - 2010-03-19:

     Updates for French language



   - 2010-03-19:

     French language updated for Definition, AuditTrail and DC



FRADEF.DLL:



   - 2009-08-17:

     Fixes an issue with the France translation of an IGSS dialog.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the French language version.



   - 2009-09-24:

     Updates to French language version



   - 2009-11-19:

     Language update for French version of Definition and Supervise is
ready



   - 2010-03-19:

     Updates for French language



   - 2010-03-19:

     French language updated for Definition, AuditTrail and DC



FRAIGSS.DLL:



   - 2009-09-24:

     Updates to French language version



   - 2009-11-30:

     Updates to French language version of IGSS Starter



   - 2009-12-03:

     Layout problems have been fixed in the French language DLL for the
IGSS Starter.



FRAJOB.DLL:



   - 2010-03-31:

     French is now completely translated in the modules: Alarm, Job
Scheduler, Maintenance 

     and User Administration. Some UI problems is also fixed in Access
Control



FRAMNT.DLL:



   - 2010-03-31:

     French is now completely translated in the modules: Alarm, Job
Scheduler, Maintenance 

     and User Administration. Some UI problems is also fixed in Access
Control



FRAUADM.DLL:



   - 2010-03-31:

     French is now completely translated in the modules: Alarm, Job
Scheduler, Maintenance 

     and User Administration. Some UI problems is also fixed in Access
Control



I2DL8.DLL:



   - 2009-09-14:

     Outgoing packets are now going to the correct place when a server
is running 

     in driver backup mode.



   - 2009-10-15:

     Data from IGSS drivers might be discarded if buffer space is
exhausted. In rare 

     cases this might even cause DC to terminate unexpectedly. This has
now been 

     fixed.  



   - 2010-01-21:

     During statup in IGSS multiuser systems the server(s) will try to
establish 

     connection to distributed PLC drivers (if applicable). Sometimes
these connection 

     attempts would fail in such a way that the connection could not be
established 

     unless the OP station running the distributed driver was restartet.
In the log 

     file I2.log on the OP station there will be entries stating that
all connections 

     are in use and thus no further connections could be made.

     

     This has now been 

     fixed.



   - 2010-02-08:

     I2DL: Connection to OP stations with distributed drivers might
fail. This has 

     previously been fixed with defect number 2010. This is an update to
the previous 

     fix.



   - 2010-07-16:

     Time services was not sending at correct intervals



   - 2011-01-25:

     TT2041 :Time services not working with DialUp and GPRS



IGSS.CHM:



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



   - 2009-12-17:

     Screen shots have been updated and layout has been corrected in
many topics.



IGSS.EXE:



   - 2009-10-21:

     Sometimes an instance of DC is left in memory. No more DC's can be
started before 

     the zombie has been removed. This has now been fixed.



   - 2009-11-13:

     When different versions of IGSS are installed Supervise may start
alm.exe from 

     the incorrect folder.



   - 2010-02-02:

     If DC is slow to stop the starter will endup restarting the system
instead of 

     completing the shutdown. This has now been fixed.



   - 2010-04-15:

     Server DC stops when OP is stopped.



   - 2010-05-18:

     Server DC stops when OP is stopped.



   - 2011-09-26:

     Description: when you have both V8 and V9 installed you need to run
a DC.EXE 

     /REG and DEF.EXE /REG before you can open the other version.

     

     IGSS will now 

     do this for you.



IGSSDATASERVER.EXE:



   - 2009-10-16:

     Graph data might be missing if IGSSDataServer is used and LOG file
size is very 

     big (10 Mb+). The problem is seen if it takes more than 1 second to
read a LOG 

     file from the report directory. The timeout has now been increased
to 10 secs.



   - 2010-09-06:

     Graphs normaly based on BCL sometimes shows invalid data when based
on log (

     only on OP and with dataserver running)



   - 2010-11-08:

     Graph based on logfiles differes when represending on server vs OP
via dataserver.

     

     This issue has now been fixed



IGSSEUT8.DLL:



   - 2009-09-15:

     When a digital object was added to a grid with the 'unit with
value' option,

      a (null) would be displayed after the digital state.



   - 2009-11-13:

     Unexplainable error messages on calculations seen when installing
certain config

     urations



   - 2010-03-23:

     The Free Value atom (ID=2) was not created in ODBC, when a digital
object was 

     based on a digital template. This limitation has now been
eliminated.



   - 2010-06-24:

     IGSS Calculation now supports the new function:

     

     SecsSinceLastUpdate('MyObject'

     )

     

     The function returns the number of seconds elapsed since *ANY* atom
on 

     the object MyObject was updated.

     

     Please note that this function only works 

     then used on a fixed time interval. It can not be used "On object
change".



   - 2011-11-17:

     New function added for calculations:

     

     STRING MyName()

     

     Returns the name 

     of the object that executes the calculation as a STRING.

     

     The purpose of this 

     function is to allow syntax like this:

     

     AnaValue(MyName())

     

     this composit 

     expression should return the (double) value of the "Free Value"
atom if executed 

     on ANY atom on a digital obejct.



   - 2011-11-28:

     Using "myName()" in calculations can cause dc troubles and make it
write exceptions 

     to the gsst.log

     This is now fixed



IGSSOPCCFG.EXE:



   - 2010-01-06:

     OPC server no longer checks for a hardlock i certain scenarios.



IGSSOPCSERVER.EXE:



   - 2009-11-12:

     OPC server in a dualised environment. When primary server dies it
will change 

     normally to secundary server. When the primary is resurrected it
failed connecting 

     to the primary server. When trying it the configured names of the
primary and 

     secondary servers are now toggled back.



   - 2010-10-06:

     OPC server didn't allow $ in tag names.

     

     IGSS OPC server has been changed 

     to allow for the following characters as initial character:

     

     "
/?+-_abcdefghijklmnopqrstuvwxyzzhsheABCDEFGHIJKLMNOPQRSTUVWXYZZHSHE[

     ]()#$&!%=|"

     

     And the following characters as the rest of the OPC tag name:

     

     

     "
/?+-_abcdefghijklmnopqrstuvwxyzzhsheABCDEFGHIJKLMNOPQRSTUVWXYZZHSHE[]()#
$

     &!%=|1234567890"



IGSSUPDATESTARTER.EXE:



   - 2010-08-13:

     Added reties to download procedure.



IGSSUT8.DLL:



   - 2010-03-25:

     The Supervise caption clock is changing from standard time to
daylight saving 

     time one hour later that the PC clock



   - 2010-11-24:

     Wildcard search in object browser did not always show correct
results.



INTERFACE.CHM:



   - 2009-10-30:

     The topic "Items available for the Object topic" under DDE and the
topic "IGSS 

     Real Time Data in Microsoft Excel" were missing or corrupt. PDF
output has  

     been created. Simply click the first item in the Table of Contents
called "View 

     Printer-Friendly Version (PDF)".



   - 2009-12-01:

     The description of the TextTypes was incorrect in the help file.
There used 

     to only three different text types. There are now 11, which are all
documented 

     in the Interface help file in the "Configuration Databases" folder.

     



   - 2010-06-16:

     1. Added new book "Web Access" to Interface Help. 3 variants are
described.

     

     

     2. Added new description of how to set up OPC with DCOM in
multiuser systems.

      This is found in the "IGSS OPC Server" book.

     3. Added new fields added to 

     ODBC tables. SUPERCONF og STANDARD: ALARMDELAYTIME and LOGTOSQL.
STRING: LOGTOSQL 

     added. ALM and ALM_ONLINE: BEG_USER and END_USER added. DSC_MAIN:
DISPLAYLAYER,

      VALUELAYER and NAMELAYER added. DSC_TEXT: BORDERSTYLE added.

     

     



INTERFACE.CHM:



   - 2010-06-25:

     In order to allow for performance improvements in ODBC, the ODBC
server is now 

     allowed to keep the configuration open indefinitely after first
use. This means 

     that subsequent connection to the ODBC server will be faster as the
configuration 

     is already loaded. 



ISLCHLM.DLL:



   - 2009-09-22:

     Updates to Icelandic language version.



ISLDEF.DLL:



   - 2009-08-17:

     Fixes a missing Islandish dialog translation that would cause IGSS
to be closed 

     as the dialog was opened.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Islandic language version.



   - 2009-09-22:

     Updates to Icelandic language version.



ISLIGSS.DLL:



   - 2009-09-22:

     Updates to Icelandic language version.



LVIDEF.DLL:



   - 2009-08-17:

     Fixes an issue with the Latvian translation of an IGSS dialog.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Latvian language version.



MNT.CHM:



   - 2010-02-17:

     The Maintenance help file has now been updated to the new
look-and-feel of the 

     IGSS V8 files. The help file is also available as a PDF file.
Simply click the 

     first item in the Table of Contents in the help file entitled "View
as Printer-

     Friendly Version".



   - 2010-03-03:

     Field help now works correctly in the Maintenance module.



   - 2010-03-26:

     When you do a search from the Search tab in the Maintenance help
file, you get 

     the message "No topics found". This has now been corrected.



MNT.CHM:



   - 2010-06-15:

     Fixed missing pdf file in Mnt.chm help file



MNT.EXE:



   - 2010-04-23:

     Maintenance is sometimes crashing when closing down



   - 2010-05-18:

     Maintenance is sometimes crashing when closing down



   - 2011-03-09:

     Dependency to Accctrl



   - 2011-05-04:

     -



   - 2012-01-27:

     New registry setting HKCU...Mnt32_HKLMReqEditPwd

     Default is 0 and everything 

     works as before

     set it to 1 and access i limited as follows

     V8:

        New object 

     and edit objects will require "definition" rights. 

        This will be the only 

     place where you can edit all descriptions. notes etc.

        Using the note and 

     description menues. You will only be allowed to edit the note,
while description 

     etc. is read only

     

     V9+:

       edit job and note entries in the "configuration"

      menu will require "definition" rights

       The entries in the "job handler" menu 

     is alrady offereing the expected functionality



NLDDEF.DLL:



   - 2009-08-17:

     Fixes a problem with a missing Dutch translation of a dialog.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Dutch language version.



NORACTRL.DLL:



   - 2009-09-02:

     Some translations were missing in the Norwegian language version.



   - 2009-09-22:

     Updates to Norwegian language version.



NORALARM.DLL:



   - 2009-09-22:

     Updates to Norwegian language version.



NORDC.DLL:



   - 2009-11-12:

     Updates to Norwegian language version



NORDEF.DLL:



   - 2009-08-17:

     Fixes an issue where a misssing translation would cause IGSS to be
closed when 

     opening a dialog.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Norwegian language version.



   - 2009-08-21:

     Layout problems have been fixed in the Norwegian version.



   - 2009-09-03:

     The Edit Event dialog box had layout problems in the Norwegian
version.



   - 2009-09-22:

     Updates to Norwegian language version.



   - 2009-09-25:

     New texts added to the Norwegian version of Definition/Supervise.



   - 2009-09-30:

     Layout problems in Norwegian version fixed.



NORIGSS.DLL:



   - 2009-09-22:

     Updates to Norwegian language version.



   - 2009-09-30:

     The text "Overvekning" has been changed to "Overvek" in the IGSS
Starter bar.

      The first text string was too long in the Norwegian version.



NORJOB.DLL:



   - 2009-09-22:

     Updates to Norwegian language version.



NORMNT.DLL:



   - 2009-09-22:

     Updates to Norwegian language version.



NORUADM.DLL:



   - 2009-09-22:

     Updates to Norwegian language version.



NORWINPG.DLL:



   - 2009-09-22:

     Updates to Norwegian language version.



ODBCIXV8SE.EXE:



   - 2010-09-06:

     Graphs normaly based on BCL sometimes shows invalid data when based
on log (

     only on OP and with dataserver running)



   - 2010-10-26:

     Multiple clients to the ODBC server while using NEVERFREE will
cause the ODBC 

     server to crash.

     

     When disconnecting an ODBC client, the list of open tables 

     is closed, also tables opened by other clients. This is fixed
through having 

     a list per connection.



   - 2011-01-04:

     Security issue in ODBC client interface



   - 2011-02-14:

     When running the ODBC server on a terminla server with multiple
operator stations 

     ODBC_Driver_HKLMIgnorePortInUse can now be set to 1, and the dialog
box will 

     no longer appear. The ODBC server will simply exit quietly.



POLACTRL.DLL:



   - 2009-09-02:

     Some translations were missing in the Polish language version.



   - 2009-09-22:

     Updates to Polish language version.



POLCHLM.DLL:



   - 2009-09-22:

     Updates to Polish language version.



   - 2009-11-12:

     Updates to Polish language version



POLDC.DLL:



   - 2009-11-12:

     Updates to Polish language version



POLDEF.DLL:



   - 2009-08-17:

     Fixes an issue with the Polish translation of an IGSS dialog.



   - 2009-09-22:

     Updates to Polish language version.



   - 2009-11-12:

     Updates to Polish language version



POLIGSS.DLL:



   - 2009-09-22:

     Updates to Polish language version.



   - 2009-11-12:

     Updates to Polish language version



POLLED.DLL:



   - 2009-10-02:

     Historical data fetched from PLC data log (when using dailed-up or
GPRS connections)

      might not work correctly if the data type of the logged data is 32
bits (e.

     g. external type: FLOAT, FP32S, FP32SWS etc). Data was retried and
shown correctly 

     - but the actual depth of the log was calculated incorrectly and
thus too few 

     historical logs was fetched from the PLCs. This has now been fixed.



   - 2010-05-25:

     Support for Grundfos CU361 devices in 7Tmod and 7Tmodgprs



   - 2010-07-16:

     Time services was not sending at correct intervals



   - 2011-01-25:

     TT2041 :Time services not working with DialUp and GPRS



   - 2011-02-10:

     Modem drivers: Some modem drivers might not be able to identify the
caller ID 

     within allowed time. This is caused by timeouts being too small. 
Timeouts have 

     now been relaxed so all modem drivers should be able to identify
the ID of a 

     remote station calling to the IGSS station due to an alarm.  This
has only been 

     verified to be a problem with the 7TS7TSA driver which in some
cases uses more 

     than 30 seconds in order to identify the ID of an incomming call.
The increased 

     timeout is now set to 60 seconds.



   - 2013-01-28:

     risk overrun buffer possible control flags lock



PRLOG.EXE:



   - 2009-10-14:

     PRLOG extended to also show IGSS Quality bits



REGISTERIGSS.EXE:



   - 2011-09-26:

     Description: when you have both V8 and V9 installed you need to run
a DC.EXE 

     /REG and DEF.EXE /REG before you can open the other version.

     

     IGSS will now 

     do this for you.



RMS.CHM:



   - 2009-11-06:

     The RMS help file has been updated to IGSS V8. A PDF version is now
available.

      Simply click the first entry in the Table of Contents named "View
as Printer-

     Friendly Version (PDF)". You can save the PDF locally, if required.



   - 2010-01-21:

     Day,  Month, Year interval not documented in RMS help file.



RMS.DLL:



   - 2009-10-14:

     Sometimes RMS showed no preview data in properties dialogue/wizard.

     There vas 

     a timeoffset between what is shown in RMS raw data and calculation
previews.

     

     RMS average reduction sometimes calculated wrong numbers.



   - 2009-10-19:

     SUM included the latest value from the previous periode Difference
and Count 

     did not take the entry value (latest value from previous peiode)
into the calcul

     ation



   - 2009-10-22:

     If report bias is set different from 0 RMS would offset reports
based on HDM 

     day values with one day



   - 2009-11-25:

     If you have edited a HDM based report item once it cannot be edited
any more.

      The data source item has been corrupted. This has now been fixed.



   - 2010-03-26:

     It can also be that confusing that preview is including any value
that have 

     same timestamp as the end time since end time is not included in
the interval 

     (it is first value of next interval)

     Anyway. The preview has been changed to 

     show these values



   - 2010-07-14:

     String output failed on Actual value reduction



   - 2010-10-04:

     RMS ignored , in numbers



RMSMENU.EXE:



   - 2010-03-10:

     RMSmenu could not start on 64bit systems



RUN.CHM:



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



RUN.CHM:



   - 2010-01-28:

     The command line examples had an incorrect syntax. There must be a
space between 

     the date/time parameter and the date/time specification. 



RUS_UPDATE.RAR:



   - 2010-03-19:

     Dialog update/fix for Russian Definition module in IGSS



RUSACTRL.DLL:



   - 2009-09-22:

     Updates to Russian language version.



   - 2010-03-31:

     Fixed some problems with the russian user interface in various IGSS
modules



RUSALARM.DLL:



   - 2009-09-22:

     Updates to Russian language version.



   - 2010-03-31:

     Fixed some problems with the russian user interface in various IGSS
modules



RUSCHLM.DLL:



   - 2009-09-22:

     Updates to Russian language version.



RUSDC.DLL:



   - 2009-09-22:

     Updates to Russian language version.



RUSDEF.DLL:



   - 2009-08-17:

     Fixes an issue with the Russian translation of an IGSS dialog.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Russian language version.



   - 2009-09-22:

     Updates to Russian language version.



   - 2010-03-26:

     Update for Russian language version of Definition module in IGSS



RUSIGSS.DLL:



   - 2009-09-22:

     Updates to Russian language version.



   - 2010-03-31:

     Fixed some problems with the russian user interface in various IGSS
modules



RUSMNT.DLL:



   - 2010-03-31:

     Fixed some problems with the russian user interface in various IGSS
modules



RUSUADM.DLL:



   - 2010-03-31:

     Fixed some problems with the russian user interface in various IGSS
modules



SETUPOPC.EXE:



   - 2010-10-05:

     When clicking 'Register' in the OPC server configuration utility
the registration 

     of two dll files would hang in memory.



SHMEMMGR8.DLL:



   - 2011-02-17:

     -



   - 2011-09-26:

     Description: when you have both V8 and V9 installed you need to run
a DC.EXE 

     /REG and DEF.EXE /REG before you can open the other version.

     

     IGSS will now 

     do this for you.



   - 2012-05-22:

     Change: the GSST.log size, so it now can grow to 20Mb



SVEACTRL.DLL:



   - 2009-09-22:

     Updates to Swedish language version.



SVEALARM.DLL:



   - 2009-09-22:

     Updates to Swedish language version.



   - 2010-05-12:

     Swedish Alarm Module Language Updates



   - 2010-05-18:

     Swedish Alarm Module Language Updates



SVECHLM.DLL:



   - 2009-09-22:

     Updates to Swedish language version.



   - 2009-11-12:

     Updates to Swedish language version



SVEDC.DLL:



   - 2009-11-12:

     Updates to Swedish language version



SVEDEF.DLL:



   - 2009-08-17:

     Fixes a problem with a Swedish dialog translation.



   - 2009-08-19:

     When opening the object properties dialog box in Definition, the
system crashed 

     in the Swedish language version.



   - 2009-09-22:

     Updates to Swedish language version.



   - 2009-09-30:

     The layout of the Data Management Definitions tab was messed up.
This has been 

     corrected in the Swedish version.



SVEIGSS.DLL:



   - 2009-09-22:

     Updates to Swedish language version.



   - 2009-10-20:

     Texts from the IGSS DLL are used in the Audit Trail module.



SVEJOB.DLL:



   - 2009-11-12:

     Updates to Swedish language version



SVEWINPG.DLL:



   - 2009-11-12:

     Updates to Swedish language version



SYNCSRV.EXE:



   - 2010-07-14:

     Object note untimely acknowledged when running server sync



SYSCONFIG.CHM:



   - 2009-09-28:

     The Search function did not work in the following help files:
Alarm, AMS, Audit 

     Trail, Dashboard, Definition, Global Help, Supervise and System
Configuration.

      This has now been corrected. At the same time, more help files are
now also 

     available in PDF format. This applies to all the above help files,
except AMS.

      The PDF output can be viewed by opening the help file and then
choosing "View 

     as Printer-Friendly Version (PDF)" at the top of the Table of
Contents.



   - 2009-10-22:

     The IGSS Data Server is now described in the System Configuration
help file.

      Search for "Data Server".



   - 2009-12-17:

     The System Configuration help file has been updated with new screen
shots and 

     improved layout in many topics.



SYSCONFIG.EXE:



   - 2009-09-15:

     When user administration was enabled leaving SysConfig with 'Save
and start 

     definition' would cause SysConfig to crash right after password
prompt.



SYSCONFIG.EXE:



   - 2010-03-05:

     Missing from previous update for defect 1756



SYSCONFIG.EXE:



   - 2011-02-18:

     -



   - 2011-04-11:

     Def: Transparancy on Gif's is shown in def after IgssUpdate. This
is now fixed



   - 2011-09-26:

     Sysconfig: Remove and add interface might fail

     

     This is now fixed.



T7T.CHM:



   - 2009-11-12:

     The T7T help file is now available in PDF format also. The PDF file
can be downloaded 

     directly from the Table of Contents of the help file. Simply click
the first 

     link - View as Printer-Friendly Version (PDF). The PDF file can be
saved locally,

      if required.



   - 2009-12-16:

     There's a help file for T7T. But previously there was no help
button on the 

     application. This has been fixed now.



TIMESPANPICKER.DLL:



   - 2009-09-15:

     Period control was not translated to local language setting



   - 2010-02-09:

     Release of new Alarm Trend Widget and multi y-axis for graph widget
for the 

     Dashboard.



TIMESPANPICKER.RESOURCES.DLL:



   - 2009-09-22:

     Updates to Polish language version.



   - 2009-09-22:

     Updates to Norwegian language version.



   - 2009-09-24:

     Updates to Czech language version



   - 2009-09-24:

     Updates to Danish language version



   - 2009-09-24:

     Updates to German language version



   - 2009-09-24:

     Updates to Spanish language version



   - 2009-10-20:

     Audit Trail and Dashboard now available in Swedish.



USERADM.CHM:



   - 2010-03-08:

     The field help did not work in User Administration. Now, when you
activate the 

     ? in the dialog boxes, a short help text appears. Simultaneously,
the help file 

     has been updated to the new look-and-feel and a printer-friendly
version is 

     now available in PDF format.



USERADM.CHM:



   - 2010-03-26:

     When you do a search from the Search tab in the User Administration
help file,

      you get the message "No topics found". This has now been
corrected.



UTIL8.DLL:



   - 2010-06-29:

     DEF Supervice sometimes crashes if Graph Axis Proberties (Period)
are changed 

     before graph appears



   - 2010-06-30:

     -



   - 2010-07-01:

     -



   - 2011-05-25:

     Def: Change of fonts in proberty table view causes def to crash,
this is now 

     fixed.



   - 2012-04-25:

     file execution from command button in supervise don't support
parameters.

     This 

     is now fixed



WINPAGER.EXE:



   - 2011-02-16:

     Alarm: Posibility to add 100 conditions in the Alarm filter



   - 2012-04-27:

     An alarm that was ended, could stop the same repeated alarm from
being acknowledged 

     by SMS.



